1. Always unplug or disconnect the air cleaner from power supply before servicing. 2. To reduce the risk of shock and injury to person, do not expose to water or rain, and do not use in window. 3. Do not use this fan with any solid-state speed control device.
EQUIPMENT: 1. Each 2.0 Flush Mount unit is equipped with two (2) eyebolts, two (2) eye-lags and industrial hanging wire for easy installation. 2. The 2.0 Flush Mount has an eight (8) foot cord and a three prong grounded plug. Electrical: 120 volts, 2.17 amps. 3. Each unit includes a years supply of filters, which consist of twelve (12) Pre-Filters, six (6) Carbon Filters and one (1) HEPA Filter.
We recommend installation be performed by a licensed contractor, licensed electrician or equivalent.
INSTALLATION: Step 1. Remove the system from the shipping container. Remove grill from intake side of system. Remove Pre-Filter and Carbon Filter. Remove plastic bag from Carbon Filter. Replace Carbon Filter, Pre-Filter (white out) and intake grill.
Step 2. On either side of the system there are two (2) mounting holes where the eyebolts are inserted. It is easiest to screw the eyebolts into these mounting holes before mounting into the ceiling. If the area above the drop ceiling is tight for space, then you may need to put the eyebolts in the mounting holes after you have the system into the drop ceiling.
Step 3. Remove the ceiling tile. The system will fit into one (1) 2x2 tile.
Step 4. A system being installed into a drop ceiling that has joists, steel girders or exposed beams above can be hung without the eye-lags (see Step 5). At least one eye-lag will be needed if your system is being installed into a ceiling that is solid above (see Step 6).
Step 5. Locate either a joist, girder or beam that is directly above the tile where your system will be installed. After you have located a joist, girder or beam, drape the industrial hanging wire over the apparatus so that either side is evenly dispersed. Line up the eyebolts with the hanging wire so they are vertical. Thread one end of the hanging wire through one of the eybolts, loop the wire and twist tightly together. Thread the opposite end of the hanging wire through the opposite eyebolt. Pull the wire tight. The system should be only slightly resting on the grid work of the drop ceiling. After you have adjusted the weight of the system on the grid work, then loop the wire and twist tightly together.
Step 6. Locate a stud in the solid ceiling that is directly above the tile where the system will be installed. Fasten the eye-lag into the stud, making sure to line up the eye-lag with the eyebolts on the system so the hanging wire will hang vertically. Thread the hanging wire through the eye-lag so that either side is evenly dispersed. Thread one end of the hanging wire through one eyebolt, loop the wire and twist tightly together. Thread the opposite end of the hanging wire through the opposite eyebolt. Pull the wire tight. The system should be only slightly resting on the grid work of the drop ceiling. After you have adjusted the weight of the system on the grid work, then loop the wire and twist tightly together.
FILTER CHANGING: 1. Pre-Filter - Replace every 3 to 4 weeks. 2. Carbon Filter - Replace at least every 2 months 3. H.E.P.A. Filter - Replace at least every 12 months
Step 1. The Pre-Filter is located behind the intake grill. Remove the intake grill by simply pushing up on the grill and removing at an angle. The intake grill is located on the opposite end of where the "2.0 Flushmount" label is found. The Pre-Filter is a blue and white polyester, pre-tack filter. the Pre-Filter is the first filter behind the intake grill. Peel away dirty Pre-Filter and discard. Install the new Pre-Filter with the white side out. Replace intake grill. DO NOT WASH PRE-FILTERS.
Step 2. The Carbon Filter is located behind the Pre-Filter. Follow Pre-Filter changing instructions from Step 1. Remove used Carbon Filter, discard and replace with new Carbon Filter. DO NOT WASH CARBON FILTER.
Step 3. The H.E.P.A. Filter is a pleated media surface with a galvanized aluminum frame, located behind the Pre-Filter and the Carbon Filter. Slip the H.E.P.A. Filter out of the sytem, discard and replace with new H.E.P.A. Filter. DO NOT WASH H.E.P.A. FILTER.
Air Cleaner location and Filter maintenance may vary according to each situation.